How to monitor the temperature and humidity of the warehouse
Warehouse is a treasure house of many enterprises, which stores a lot of important materials and products, so the work of fire prevention and anti-theft is very important to avoid the occurrence of fire. So how to monitor the temperature and humidity of the warehouse. The following article is a small series for everyone to introduce in detail.
Warehouse temperature and humidity verification
After the manager has stored the warehouse equipment in a timely manner, we can properly monitor the temperature and humidity of the warehouse.
Need to pay attention to the following aspects:
The temperature and humidity verification should be based on the stacking height of the warehouse materials and products, taking into account the layout of the warehouse doors and windows, the location of the temperature and humidity control facilities, and other factors affecting the temperature and humidity. If necessary, set the monitoring points at different heights of the warehouse space. .
Temperature and humidity inspections* are good at the harsh weather of the year*, usually the extreme conditions of the *hot and *cold stages in summer and winter.
The temperature distribution should be separately investigated in separate rooms and floors.
Warehouse temperature and humidity verification example
Storage conditions: a finished product warehouse, temperature ≤ 20 ° C, no specific requirements for relative humidity.
Verification purpose: verify the uniformity of temperature and humidity distribution in the warehouse and the temperature and humidity table * good suspension position to meet the requirements of the product for the storage environment.
Monitoring time: According to the local climate characteristics, July to August is the hot month of the year, so the confirmation time for the warehouse is from July 1st to July 15th, and continuous monitoring is 15 days.
Sampling frequency: Recording is performed twice every day from 10:00 to 11:00 in the morning and from 14:30 to 15:30 in the afternoon. After the temperature and humidity of the room are relatively balanced, the temperature and humidity of each detection point are recorded and recorded continuously for 15 days.
The monitoring point is determined: generally, uniformity layout and special location layout should be considered. The principle is to cover the effective storage space of the entire warehouse and distribute symmetrically and evenly within the warehouse space.
Usually the locations of the outlets are: air conditioning vents, high and low locations in the general inventory area, and exits to the non-temperature controlled area (loading dock or transit storage area)
Export (comparing indoor and outdoor temperatures)
Reprinted from the network